Multicore SWA Armored, XLPE insulated, PVC sheathed
0.6 / 1 KV POWER CABLES Conforming to IEC 60502-1
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60502-1
This specification covers XLPE insulated, circular or shaped, multicore armoured cables, rated at 0.6/1 KV according to IEC 60502-1 for use indoors, outdoors, in cable ducts and for direct burial underground, where severe mechanical stresses are present.
Plain, annealed electrolytic copper conductors, circular stranded, or sectoral stranded, conforming to the applicable requirements of IEC 60228.
XLPE thermosetting material, conforming to the applicable requirements of IEC 60502-1.
Insulated conductors are laid up, filled where necessary with non-hygroscopic material and covered with an extruded thickness of thermoplastic material.
Galvanized round wires completely covering the assembly of cores complying to the applicable requirements of IEC 60502-1.
PVC based thermoplastic material, conforming to the applicable requirements of IEC 60502-1.
Conforming to the applicable requirements of IEC 60502-1 either on Raw materials or on finished products.
|Armour type||Galvanized steel wires|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Flame retardant||IEC 60332-1-2|
|See all products|