Country ref. EXW 1*95
StandardsInternational : IEC 60228; IEC 60332-1-2; IEC 60502-1
This specification covers PVC, circular, single core armoured cables, rated at 0.6/1 KV according to IEC 60502-1 for use indoors, outdoors, in cable ducts and for direct burial underground, where severe mechanical stresses are present.
Plain, annealed electrolytic copper conductors, circular stranded, conforming to the applicable requirements of IEC 60228.
XLPE insulation, conforming to the applicable requirements of IEC 60502-1.
Aluminum wires armor, complying to the applicable requirements of IEC 60502-1.
PVC based thermoplastic material, conforming to the applicable requirements of IEC 60502-1.
Conforming to the applicable requirements of IEC 60502-1 either on Raw materials or on finished products.
|Number of conductors||1|
|Conductor flexibility||Stranded class 2|
|Armour type||Aluminium Wire|
|Nominal insulation thickness||1.1mm|
|Nominal armour wire diameter||1.7mm|
|Nominal outer sheath thickness||1.6mm|
|Nominal overall diameter||21.0mm|
|Rated Voltage Uo/U (Um)||0.6/1 kV|
|Max. DC resistance of the conductor at 20°C||0.193Ohm/km|
|Permissible current rating in open air||327A|
|Permissible current rating when buried||317A|
|Operating temperature, range||-15 .. 55°C|
|Installation temperature, range||-5 .. 50°C|
|Ambient air temperature||30°C|
|Maximum operating temperature||90°C|
|Short-circuit max. conductor temperature||250°C|
|Flame retardant||IEC 60332-1-2|